You can use the DIP switches on the Synergis™ Cloud Link to run hardware commands.
Available DIP switch commands
There are four DIP switches on the Synergis™ Cloud Link labelled 1 to 4. To run a command, set the DIP switches as indicated in the following table and press the EC button for one second. If the code is valid, the status LEDs will flash green for the process of the command, otherwise they flash red for one second. Synergis™ Cloud Link automatically performs a software restart after you have run a command.
Softwire 11.0 and later:
Resets the Synergis™ Appliance Portal
logon password to factory default
Softwire versions earlier
than 11.0: Resets the Synergis™ Appliance Portal logon password
to factory default (
|ON||OFF||OFF||OFF||Resets all settings to factory default. This command has the
NOTE: The unit firmware is not affected by this command.
|OFF||OFF||ON||OFF||Re-enables the ability to change output states from the I/O diagnostics page of the Synergis™ Appliance Portal.|