Readers connected to the MR62e downstream panel must be addressed and used in specific pairs to work.
The following table shows the required reader address configuration:
|Reader number (address)||Door setup||Mercury turnstiles and elevators|
|0||Door 1: Reader side IN||Yes|
|1||Door 2: Reader side IN||Yes|
|2||Door 1: Reader side OUT||No|
|3||Door 2: Reader side OUT||No|
NOTE: To use the MR62e to control only one Card In/Card Out door, use addresses 0 and 2.
To use the MR62e to control two Card In/REX Out doors, use addresses 0 and 1.