To establish communication between the Synergis™ unit and the connected interface modules, you need to configure them in Synergis™ Appliance Portal.
Before you begin
What you should know
- Log on to the Synergis™ unit.
.The portal shows the hardware tree as three columns: The first column displays your configured hardware manufacturers and the number of channels they use. Click on a hardware manufacturer to bring up its channels in the second column. Selecting a channel brings up the interface modules connected to this channel in the third column. The second column changes to match the hardware selected in the first column, and the third column changes to match what is selected in the second column. You can edit (), clone () or delete () the channel by rolling over it and selecting from the icons that appear.
- At the top of the Hardware column, click Add ().
In the Add hardware dialog
box, select the Hardware type, the
Channel, and the rest of the
interface module properties, which depend on the hardware type you selected.
In the same dialog box, add all interface modules connected to the same channel as
- To add the interface modules manually, click Add.
- To discover the interface modules, click Scan.
The discover feature finds all interface modules from the same manufacturer that are connected to the same channel and adds them to the list. For this to work, all of the interface modules must use the same baud rate and be configured with a different physical address.
The hardware type, channel, and interface modules you added are displayed in the hardware tree.
For each interface module you added, select it from the hardware tree, and configure its
settings in the window that opens.
For the description of these settings, refer to the manufacturer’s documentation.
- At the bottom of the page, click Save.