Synergis™ Cloud Link is an intelligent and PoE-enabled access control appliance of Genetec Inc. that supports a variety of third-party interface modules over IP and RS-485. Synergis™ Cloud Link is seamlessly integrated with Security Center and is capable of making access control decisions independently of the Access Manager.
Synergis™ Cloud Link and accessories can be housed inside an enclosure that are part of a Synergis™ IP access control system.
The optional expansion module offers additional RS-485 ports and three SAM card slots for increased security. For more information on the expansion module, see the Synergis™ Cloud Link Quick Start Guide.
|Hardware feature||What you should know|
|A||RS-485||Four embedded RS-485 communication ports (or channels) named A,
B, C, and D. The
number of interface modules you can connect to each channel
depends on the type of hardware you have. In configurations
where interface modules only use an IP connection, the four
RS-485 ports are not needed.
NOTE: When you start an RS-485 bus from the Synergis™ Cloud Link for HID module communication, you must set the associated termination DIP switch to ON. You must also set the termination jumper on the last connected module on the RS-485 bus.
|B||USB1 and USB2||For maintenance use.
NOTE: This connection has not been evaluated by UL and is not to be used if UL Listed access control system compliance is required and is to be maintained.
|C||LAN1 and LAN2||Two Ethernet LAN ports are provided for connection to the IP network.
NOTE: Synergis™ Cloud Link can be powered using an Ethernet connection (PoE).
NOTE: Connecting to Security Center through the LAN 2 port has not been evaluated by UL and is for supplementary use only.a
|D||Status LEDs||Synergis™ Cloud Link LED feedback.|
|E||Power||Connect Synergis™ Cloud Link to an external 12 VDC (nominal) power supply.|
|F||Code DIP switches||Set a command code with the DIP switches, and run the command by holding the EC button for one second. If the code is valid, the status LEDs will flash green for the process of the command, otherwise they flash red for one second. Synergis™ Cloud Link automatically performs a software restart after you have run a command.|
|G||Service port||Internal use only.|
|H||DEP. IND.||Deported indicators were not evaluated by UL, and are not to be used if UL Listed access control system compliance is required and is to be maintained.|
|I||Monitoring inputs||Monitoring inputs were not evaluated by UL, and are not to be used if UL Listed access control system compliance is required and is to be maintained.|
1For ULC-S319 compliant installations where Mercury EP controllers are located in a separate enclosure from the Synergis™ Cloud Link, communication cabling must be completely shielded. The network cabling used for communication with the controllers via the Synergis™ Cloud Link's LAN1 or LAN2 port must be CAT5e (shielded twisted pair) or better. This applies to all involved cabling segments between the Synergis™ Cloud Link and the network switch, and between the network switch and the Mercury EP controllers.